Partial heat recovery can be used in applications where hot water is needed for use in kitchens, lavatories, industrial process etc. It is comparatively smaller in size and its heating capacity is not controlled.The partial heat recovery heat exchanger cannot operate alone without a load on the chiller. The partial heat recovery heat exchanger can get up to 70°C leaving temperature.
A Total (100%) Heat Pump is serve as a normal air cooled chiller & heat pump unit and hot water heat pump as well. Total (100%)Heat Recovery heat Pump is capable to produce chilled water and hot water to meet both the cooling and heating demand simultaneously for the air-conditioning system and hot water system. The Total (100%) Heat Recovery Heat Pump is designed to cool chilled from 12℃ to 7 ℃ and heat hot water up to 65℃ simultaneously, it consist of compressors, air heat exchanger (condenser coil), two numbers of water side heat exchangers for chilled water and hot water respectively, necessary numbers of electronic expansion valves and intelligent electronic refrigerant flow control and all necessary accessories.